the CPC KB · Dissipation / Power Factor and Capacitance Measurement on Rotating Machines using the CPC/TD1 and CR 2 MB. OMICRON. CPC Reference Manual. PRIMARY TEST SYSTEM. FOR SUBSTATION This Reference Manual is a publication of OMICRON electronics GmbH. All rights . View and Download Omicron CPC user manual online. CPC Test Equipment pdf manual download.
|Published (Last):||8 December 2013|
|PDF File Size:||6.1 Mb|
|ePub File Size:||1.72 Mb|
|Price:||Free* [*Free Regsitration Required]|
This way, the CPC high-current outputs represent the “amplified” Quick test card directly.
Page 68 This setting is suggested if the operator suspects, for example, an incorrect functioning or an operational malfunction of CPC Contact us News Press Legal Imprint. Your system maanual will provide you with a valid static IP address.
Omicron CPC 100 User Manual
This signal can either be a voltage or a current signal from CPCand has a signal characteristic similar to a saw-tooth signal with a different steepness for the rising and the falling slope. Don’t have an account? Ct Burden From these measurements, the burden in VA and the power factor cos calculated. To print the manual completely, please, download it.
CT Excitation test card – using the crosshair cursor The final step of the test is the test assessment. In order to determine the true CB closing time value, these ms need to be deducted from the value displayed in the measurement table refer to the following examples.
OMICRON CPC REFERENCE MANUAL Pdf Download.
View selector Test Card View default view upon start-up View to set ommicron test cards, compose test procedures, enter test settings, define test cards or the test procedure default, start tests etc.
During the hardware and software mxnual phase, the software displays a splash screen. Open the catalog to page 2. Service saving settings to R Current Transformer Figure 5: The Online Industrial Exhibition. The R button renews the display of the left-hand side pane.
The output current of the CPC can be increased up to A by means of an electronically controlled current booster. Apart from the pull-down menus and the toolbar, CPC Explorer interface consists of three panes: Get your local contact Find contact. TR Ratio test card with test results Navigate to the parameter fields, and enter the values according to your test requirements: Enter text from picture: Page 28 CPC V 3.
Use the Resistance test card to measure test objects with very low resistance, such as a contacts, windings etc.
Current Transformer Measurements Vsec: Others – Ramping For each ramp, a trigger signal can be specified to prematurely terminate this cp and execute the next one. Creating Defaults And Templates Note: A possible license file upgrade is handled the same way as a CPC software upgrade.
Designated Use Preface Designated Use CPCin conjunction with its accessories or as a stand-alone unit, is a multi- purpose primary test set for commissioning and maintaining substation equipment. This example shows how the three current outputs of a CMC test set are led to the synchronization inputs I AC of three CPC test sets to drive their high-current outputs. Changing Fuses CPC The last measured values are “frozen”, and can now be assessed.
CPC – Documents – OMICRON
Don’t show me this message again. With the CPC Page Voltage Transformer 2.
Before disconnecting from CPCconnect the device under test to protective earth. Page 94 CPC V1. Trim protruding screen strands, and coc the cable assembly into the housing, orientating the guides to the slots.