Buy Gefran PID Temperature Controller, 96 x 48 (1/8 DIN)mm, 2 Output Relay, V ac, V ac Supply Voltage ON/OFF RR Browse our. setting up the Gefran controller for the application referenced above. Additional software and hardware configuration information can be found in the User’s. Gefran controllers are built with SMT technology. The instrument provides a complete operator interface, protected by a Lexan® membrane that ensures.
|Published (Last):||27 October 2006|
|PDF File Size:||15.29 Mb|
|ePub File Size:||10.80 Mb|
|Price:||Free* [*Free Regsitration Required]|
It can signal variations in load input by identifying the current value in ammeter input in the range For even simpler configuration, you can use a PC programming kit consisting of a cable and a guided program for Windows environment. Thermon South Africa Pty Ltd. This manual also for: Notes concerning electrical safety and. It is particularly in combined Heat-Cool control applications where the advanced algorithms come into play, allowing an extremely narrow band between heating and cooling without causing overlap.
It is enabled by means of configuration code AL. An additional output 24VDC, 30mA max.
Navigating through the controller menu. Manual Tuning A Enter the setpoint at its working value. The instrument provides up to 4 outputs: The yefran entire programming procedure is made easier by grouping the parameters in function blocks CFG for control parameters, Inp for inputs, Out for outputs, etc. The purpose of a temperature control loop is to maintain the process temperature accurately at a determined level. Level 1 display Menu The instrument provides up to 4 outputs: Page 21 [ gfg ] c.
Navigating through the Controller Menu Keep pressed down to scroll through the menus in sequence and release it when the required menu appears.
Advice for gerfan installation. Page 22 This menu makes it possible to configure the various parameters that control serial communication between the controller and the supervisor.
In this way, you just have to set the setpoint and the alarm, then launch self-tuning with the specific button. With scale settable in limits: An analog output in voltage or in current is also available. S Minimum limit of main input scale Min Manual Tuning If the Integral Time value is too long Weak integral actiondeviation between the controlled variable and the set- point may persist.
Add to my manuals Add. In addition to the control and alarm outputs, you can also have outputs that repeat the state of the digital or retransmission input by process variable, setpoint, deviation, alarm trip points and values acquired via serial line.
Example of connection with TC input.
Alarm 1 Alarm 2 Alarm 3 AL. A second auxiliary analog input from current transformer is available. Integral heating time [0.
Gefran 1200 Instructions For Use Manual
It continuously reads system oscillations, immediately seeking the PID parameter values that reduce the current oscillation. R Digital from serial line Absolute Def. Press to access the parameters of the selected menu. Level 1 Display Menu Accuracy better than 0. Input Virtual instrument inputs S. To print the manual completely, please, download it. Gefran Temperature Controller: Page of 40 Go.
Enhanced software and hardware allow a high degree of user configurability. 12000 Gefran is a high performance configurable controller, widely used in industry for processes involving transmitters 4…20mA, 0…10V and temperature sensors.
Cencal Memory Map – Description Universal input configurable from faceplate Accuracy better than 0. The main input for the variable to geran controlled is universaland allows connection of a wide variety of signals: Clicking on a tag will display a list of all products with that tag applied.
The functions of each output are freely configurable from the faceplate.
GEFRAN INSTRUCTIONS FOR USE MANUAL Pdf Download.
InP Input settings third menu to set up This menu makes it possible to configure the parameters for the Controller input signals. Know what the controller is doing: Keep to return immediately to level 1. Configuration And Programming Integral heating time [0. Warnings and instructions for. Inputs and outputs connection. The instrument is supplied with an “EASY” configuration calling for just a few parameters only those pertaining to the model ordered and essential to the egfran operation.
Max value associated with the input selected with the TYP parameter Ki.